Low Voltage Disconnects
Discharging batteries beyond a critical low voltage can damage the batteries and/or load, and require a longer recharge interval. A low voltage disconnect prevents this condition. The LVD contains a sense and control circuit housed in a compact, rugged, vinyl-clad aluminum case. It is installed in-line between the battery and the load. The unit continually monitors battery voltage and if it falls below a preset voltage threshold, the load is automatically disconnected. When batteries are recharged past another pre-set voltage the load is reconnected. Connect and disconnect points are user adjustable.
|Factory Set Actuation Points||Adjustment Range|
|LVD 12-30||12V (Neg Ground)||30 Amps||10.4 VDC||12.2 VDC||9 – 15 VDC|
|LVD 12-75||12V (Neg. Ground)||75 Amps||10.4 VDC||12.2 VDC||9 – 15 VDC|
|LVD 24-50||24V (Neg. Ground)||50 Amps||21.0 VDC||24.5 VDC||18 – 30 VDC|
|LVD 48-30||48V (Pos. Ground)||30 Amps||42.0 VDC||49.0 VDC||38 – 60 VDC|
Operating Temperature: 0 – 50 °C
Dimensions (mounted vertically, all models): 5.25” High x 5.25” Wide x 3.5” Deep
Weight: (All models): 2 Lbs.